Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Published (Last):||27 February 2015|
|PDF File Size:||17.66 Mb|
|ePub File Size:||3.83 Mb|
|Price:||Free* [*Free Regsitration Required]|
Allow 50 mm 2 in. Secure the template to the mounting surface. Follow these steps to connect the replaceable battery. Follow these steps to install your controller on the DIN rail. The Battery Low indicator on the LCD display of the controller shows the status of the replaceable battery. You can also contact a special Customer Support number for initial help in getting your product up and running.
Replacing the battery when the controller is powered down will lose all user application memory. Output 2, 3 and 4 may be used like 1676 other FET transistor outputs, but in addition, within a limited current range, they may be 7166 at a higher speed. At this level transient voltages are controlled and do not exceed the impulse voltage capability of the product’s insulation.
Secure any external connections that mate to this equipment by using screws, sliding latches, threaded connectors, or other means provided with this product. Make sure your controller is spaced properly see Controller Spacing on page 12 for more information.
Wear an um010 grounding wriststrap. Be sure that power is removed or the area is nonhazardous before proceeding.
Wire fragments that fall into the controller could cause damage. Follow these guidelines when you handle this equipment: For more information on proper grounding guidelines, see the Industrial Automation Wiring and Grounding Guidelines, publication The input and output terminals of the MicroLogix controller are designed for the following spade lugs.
1766-IN001 – Rockwell Automation
Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. Follow these steps to install your controller using mounting screws. United States Contact your distributor. For more information on proper grounding guidelines, refer to the Industrial Automation Wiring and Grounding Guidelines, publication If it is open, close the DIN latch.
Outside United States Please contact your local Rockwell Automation representative for the return procedure. Be sure that the area is nonhazardous before proceeding. Run the ground connection from the ground screw of the controller to the ground bus prior to connecting any devices.
IN – Rockwell Automation
Hook the top slot over the DIN rail. For u0m01, when using a real-time clock RTC. Plug the ribbon cable connector into the bus connector. Do not touch connectors or pins on component boards. Place a flat-blade screwdriver in the DIN rail latch at the bottom of the controller. The controller can be mounted to ENx7. However, if your product is not functioning and needs to be returned, follow these procedures.
Specifically, this equipment is intended for use in clean, dry environments Pollution degree 2 1 and with circuits not 176 Over Voltage Category II 2 IEC 3.
The terminals will accept a 6. Refer to the mounting template inside the back cover of this document. Vertical mounting is not supported due to thermal considerations. You must provide a Customer Support case number call the phone mu001 above to obtain one to your distributor in order to complete the return process. Use a power supply that matches the transmitter specifications as shown. When you connect or disconnect the battery an electrical arc can 176.
When using spade lugs, use a small, flat-blade screwdriver to pry the finger-safe cover from the terminal blocks, then loosen the terminal screw.
Finger-safe cover TIP If you wire the terminal block with the finger-safe cover removed, you may not be able to put it o on the terminal block if the wires are in the way.
Trademarks not belonging to Rockwell Automation are property of their respective companies. By using suppression, you also reduce the effects of voltage transients caused by interrupting the current to that inductive device, and prevent electrical noise from radiating into system wiring. Do not touch circuit components inside the equipment. You must also provide an acceptable grounding path for each device in your application.
No patent liability is assumed by Rockwell Automation, Inc. Several specific steps can be taken to help reduce the effects of environmental noise on analog signals: Use a static-safe workstation, if available.
Tighten the terminal screw, making sure the pressure plate secures the wire. Wiring Your Analog Channels Analog input circuits can monitor voltage signals and convert them to serial digital data ej shown in the following illustration. Debris strip ATTENTION Do not remove the protective debris strip until after the controller and all other equipment in the panel near the controller are mounted and wiring is complete.
Make sure that the MicroLogix system is properly grounded. Each product is supplied with markings o the rating nameplate indicating the hazardous location temperature code. For more information, contact your local distributor or Rockwell Automation representative, or visit http: Mount your DIN rail.